Associates & Distributors
AMTWAF Design One
AMTWAF Design Two
Combined Treatment 1
Combined Treatment 2
Combined Treatment 3
Combined Treatment 4
Combined Treatment 5
Combined Treatment 6
Car Wash ETP
Rice Mill ETP
Full Scale Pilot Plant
ETP Enquiry Form
Water Analysis Report
Effect Of Aeration
Micro Bubble Generator
Solids Removal Filter
Sediment Removal Filter
UF Membrane System
UF Operating Condition
PVDF UF Membrane
PP UF Membrane
PVC UF Membrane
UF Operation Manual
Automated UF Skid
Small Community System
Micro Bubble Enriched
Hand Pumped System
Small Municipal System
Automated Micro Bubble Enriched
How Evapo-Rust Works
Typical Client List
How To Use
Cooling System Cleaner
Mode of Action
Toxicity of Nano-Silver
Sanitation & Hygeine
MSW & Other Bio-Wastes
Water & Wastewater
Oil Spill Management
Soft Drinks Mfg.
Providing Sustainable Green Technology Solutions
Operating temperature range: 5-45º C
Maximum free chlorine concentration in cleaning solution is 1000 ppm for PVDF membranes,
3000 ppm for PP Membranes and 200 ppm for Modified PVC & PES Membranes.
In raw feed water maximum allowable free Chlorine concentration is 200 ppm for PVDF membranes, 300 ppm for PP Membranes and 150 ppm for modified PVC and PES membranes.
Viscosity in inlet feed water is ≤12 cp.
COD at inlet in feed water is ≤ 500 ppm.
BOD at inlet in feed water is ≤ 500 ppm.
SS at inlet in feed water is ≤ 200 ppm.
Back To Top
Mode of operation In wastewater treatment:
We use outside to in form of filtration in cross flow mode to minimize the chance of clogging of the membrane modules.
Pressure Release Valve and electrical Pressure Switch is provided on the skid to avoid pressure build ups which may cause bursting of the hollow membrane fibers.
Feed water is inserted through an inlet spout into the membrane module body.
Special Potting Design gives strength to the membrane assembly.
Produced water is collected by two ports at both ends through the end caps.
pH range: 3-10 (2-12 when doing cleaning).
input water turbidity: 15NTU Max.
Max. feed water pressure: 0.20 MPa
Pretreatment filter mesh size: ≤ 50 micron.
Oil concentration in raw water must be < 2 mg/L, otherwise it must be removed by pretreatment.
Synthetic Oil in wastewater should be NIL.
Design pure water flux: Check the module specification.
Max. TMP (Trans-Membrane Pressure): 0.15MPa
(chemical cleaning is needed when TMP is more than 0.1MPa).
UF Membrane Operating Conditions
View on Mobile